Where is my filter and how often should I change it?
I want to upgrade my thermostat but don't know what to look for!
I have a question about my repair
How does my heating and cooling system work?
Indoor Air Quality?
Where can I find my manual?
Some rooms are too cold!
Some cooling systems develop a musty, unpleasant smell when they run in cooling mode for the first time after a season or sometimes after installation.
This is commonly known as "dirty sock syndrome" in most cases and it is related to microbial activity in you evaporator coil, in most of the cases you cannot see growth on the surface of the evaporator coil but your nose can definitely tell.
This happens most of the times in heat pump systems rather than furnaces, since temperatures in gas fired furnaces exceed 160 degrees which kills micoorganisms. Temperatures at the evaporator coil in heat pumps are between 105 to 130 degrees, making this pleasant for microorganism activity.
So what can you do to alleviate this?
Ice Around Your Heat pump
During the heating season you might see ice around the coil of your outdoor system, this happens usually when the temperature outside drops below 42-45 degrees and there is enough moisture in the air to produce ice. While your heat pump is running in heat mode, the outside air is used as part of the refrigerant cycle since it helps convert liquid refrigerant into a gas as it goes through the outdoor coil, that's the purpose of the top condenser fan motor, to move air across the coil. In this case, the air coming from the top is at least 10 degrees colder than the air going in through the sides.
So if we are at 42 degrees outside the temperature of the air going through the outside coil is about 32 degrees or lower and that is when ice starts to build around your system.
The Defrost Cycle
Your heat pump comes with a built in defrost cycle that is triggered by an outdoor sensor, runtime and a coil temperature sensor, if the system detects that a defrost cycle is needed you will see this happen:
Before the defrost cycle
During the defrost cycle
During the defrost cycle
Things To Look For
One of the most common things to look for during a cold rainy day is ice building on the top of your heat pump, this happens when water drips from the edge of your roof right over your heat pump. This causes that loud banging noise that sounds like your outdoor system is falling apart or a piece of metal fell off and started bouncing in there. Most of the times it is small pieces of ice breaking down and hitting the fan blades, some systems accumulate enough ice that it builds a hard layer around the fan blade causing them to get stuck and cause one of the following problems:
If this happens, switch your system to Em (emergency or auxiliary heat) mode on your thermostat, this will turn off the outdoor system during the heating cycle and will start using only the electric heat (located at your indoor system) to heat your home.
You will need to talk to your roofer or a handyman to install a rain guard or drip guard (unless you want to install rain gutters), it is a piece of sheet metal that will prevent water from falling over your condenser and causing damage.
© 2018 Airco